Daily Field Report
The site was visited by Rasheen Biggins AS Engineering and Consulting (ASEC) representative for the purpose of providing quality control inspection and testing services. Visual observation techniques were employed to assure compliance with project drawings/specifications, applicable codes, and materials submittals. The following observations were made on site today
Upon arrival to the project site, our representative observed work was already in progress. The contractor continued placing fill along the dam area with lift thicknesses being under 8 inches or less. A CAT bulldozer spread fill materials brought by two CAT Dump trucks which were then compacted using a CAT 825K landfill compactor. Density tests were performed on the fill placed. Based on the density test results, visual observation of the material placed and random probing of the placed lifts, the fill placed was found to meet job specifications for compaction. Density tests were reported back to the contractor and results can be found in the attached density test report. A Troxler nuclear gauge #38069 was used.