Daily Field Report
As requested, the site was visited by our AS Engineering and Consulting (ASEC) representative for the purpose of providing quality control inspection and testing services, visual observation techniques were employed to assure compliance with project drawing/specifications, applicable codes, and materials submittals. The following observations were observed on site this day.
The placement and compaction of the sewer trench with GAB between MH1 and MH6 and recycled GAB between MH2 and MH3 continued this day.
At the time of arrival, our representative observed that work was in progress with placement continuing to 1 foot below finished grade and compacted using a trench compactor.
Density test results indicate that the compacted materials met the project requirement of 90% (and 95% at finished grade).